We attended site for a call out to repair broken down LT (low temp) Coldroom. The problem was due to short on refrigerant because of a leak upon the silver solder join upon compressor suction service valve. The system was de-commissioned, leak repaired, filter drier, solenoid valve with coil & sight glass replaced, system tested with re-commissioning and back operational same day.
Upon same visit Charles MT (medium temp) system was not operational & hadn’t been for some time due to cost. He had been advised the system required replacing due to failed compressor. We tested & compressor was fine. Within pictures you will see electrical components failed of start relay, start & run capacitor all corroded due to weathering of insufficient house because electrical box not IP rated. We replaced components with drier, solenoid & sight glass, whilst also repairing low refrigerant leak upon expansion valves faulty flare. We repaired all the necessaries, tested system, re-commissioned and operational same day of LT Coldroom.
Another satisfied customer.